Chapter I General provisions article in order to improve fire safety fire risk management to prevent serious fire accidents and protect personal and property safety, maintaining public security, in accordance with the People's Republic of China fire protection law and other laws and regulations, combined with the facts of the province, these provisions are formulated.
Article the fire safety management of provincial administrative areas at high risk of fire units, these provisions shall apply. This provides by said fire high-risk units is refers to following units and places: (a) building total area 20,000 square meters above or underground area 10,000 square meters above of Mall, and market; (ii) building total area 3000 square meters above or underground area 1000 square meters above of public entertainment; (three) building total area 20,000 square meters above of library, and public gallery, and Museum; (four) building total area 20,000 square meters above of track traffic station, and bus station, and railway station, and civilian airport, and
Terminal of waiting room, and Terminal, and houchuanting; (five) area 10,000 square meters above of methyl, and b class solid, and can burning fiber production, and processing, and store Enterprise; (six) building height over 100 meters of senior public building; (seven) audience Office seat number 30,000 a above of stadium Museum, and Hall; (eight) rooms total 200 a above of hotel, and hotel; (nine) bed total 200 Zhang above of hospital, and nursing home, and orphanage; (ten) bed total 1000 Zhang above of boarding school;
(11) bed total 150 Zhang above of boarding nursery, and kindergarten; (12) c class material production processing workshop employees total 1000 people above of enterprise; (13) design total reserves 10,000 cubic metres above of methyl, and b class gas, and liquid of production, and filling loaded, and store, and sales Enterprise; (14) used wood or brick wood of national focus heritage protection units; (15) Province Government determine of other personnel intensive places, and flammable easy burst places, and senior and underground public building, units.
Third fire risk unit within the administrative area of people's Governments at various levels shall be responsible for the fire.
Public security organs of the people's Governments above the county level shall supervise fire-risk units within their respective administrative areas, by public security fire control institutions responsible for its implementation.
The people's Governments above the county level functions, industry systems department responsible within the scope of their respective duties on fire risk of fire safety management.
Fourth fire risk unit should strictly carry out laws, regulations, rules and regulations unit of the fire risk of fire safety duties.
Chapter II fire risk of fire safety management of the fifth article of the statutory representative or fire safety responsibilities who is in charge of the unit, this unit has overall responsibility for fire safety work.
Fire fire safety in high-risk units responsible should have their own fire safety, fire safety work in regularly every year to study the unit, for the fire safety of the unit to provide the necessary financial resources and organizational guarantees.
Sixth fire units fire safety management should be identified at high risk people, organizing the implementation of the fire safety management of the entity.
Fire fire safety management in high-risk units shall regularly organize and implement fire safety inspection at least once every month to report fire safety responsibilities once the fire safety condition of the entity.
The seventh fire units fire management agencies should be identified at high risk, equipped with fire-fighting strength of the unit suitable for professional fire management staff.
Fire-risk units Allied fire management personnel should be in accordance with the laws and regulations of fire safety inspections, inspections and fire education and training.
Eighth fire-risk units shall in accordance with the law provides for the establishment of a full-time fire department. Does not need to establish a full-time fire department fire-risk units according to law, shall establish a volunteer fire department.
Volunteer fire fighter should be the number of fire-fighting and emergency evacuation requirements configured units but shall not be less than the total number of staff of the 20%.
Fire-risk units of full-time and volunteer fire brigades should be in accordance with the relevant standards or according to the actual need to be equipped with fire-fighting equipment, equipment, training and fire emergency evacuation drills on a regular basis.
Nineth fire-risk fire service control rooms of units should be by automatic fire fighting system operators on duty 24 hours, and not less than 2 persons per class, working hours may not exceed 8 hours in a row.
Tenth fire fire safety in high-risk units responsible, Manager, professional fire management staff, automatic fire protection system in operation, as well as full-time and part-time firefighters and electricians, welders and other special types of personnel should be subject to fire a professional training, automatic fire extinguishing system for personnel should be obtained in accordance with regulations of the State fire service professional qualifications accordingly.
11th fire fire safety management personnel in high-risk units determine or change the date in the 5th through to area fire safety information management system of public security fire control institutions record.
12th fire risk unit to use the buildings and sites shall conform to the national standard, and fire regulations.
Fire-risk units use buildings and sites without acceptance, checking conformity of public security fire control institutions shall not put into use has been put into use, should be discontinued.
13th fire risk unit configuration fire control facilities and devices in accordance with State provisions.
High-rise building fire-risk units should be in accordance with the technical standards set on fire shelter, escape facilities, equipped with escape, self-help equipment such as gas masks, descending.
14th fire risk unit electrical wiring, gas piping, construction should be subcontractors with appropriate qualification of construction enterprises in accordance with law.
15th fire automatic fire-fighting equipment in high-risk units should be networked with the remote monitoring system of city fire safety, and to ensure normal operation of networked devices. 16th article fire high-risk units of following parts or facilities should set obviously of identifies signs: (a) Fire Lane, and fire engine ascended job site, fire dedicated channel, and site; (ii) fire control room, and fire water pumping station, and owned generator room, and anti-row smoke room, fire facilities equipment with room; (three) fire hydrant, and fire extinguisher, and pump combined device, fire facilities, and equipment configuration, and set points near; (four) fire door, and fire volume curtain, and fire alarm, fire facilities linkage control button near; (five) fire pump, and
Fire protection piping, fire line near the fire service equipment such as valves or components; (vi) shall be indicated in other uses, fire-fighting facilities, equipment and how to use where appropriate.
17th units belong to the high risk of fire in public assembly places, selling inflammable and explosive dangerous goods are produced and stored enterprises shall, in accordance with the relevant provisions of participating in fire and public liability insurance.
18th fire-risk units shall entrust a qualified each year's technical services unit fire equipment to conduct a full inspection, and the date of receipt of the test report in the 5th through to area fire safety information management system of public security fire control institutions record.
19th fire risk should be routine maintenance of fire-fighting facilities, equipped with automatic fire-fighting equipment shall entrust a qualified technical service regular maintenance of automatic fire-fighting equipment, and maintenance through to area fire safety information management system of public security fire control institutions record.
20th article implementation of the fire risk of fire safety assessment system, and the specific measures formulated by the provincial public security organs according to the relevant regulations of the State. 21st fire-risk units shall establish implementing internal chain of fire safety system and post fire safety responsibility system, signed fire safety responsibility step by step every year.
Fire safety unit owner, managers, heads of departments, responsibility, modification, shall, on the date of the change in the 5th sign a new fire safety responsibility.
The 22nd fire risk shall be in accordance with State regulations, establish and perfect the system of fire safety and fire safety procedures, and announced the implementation. 23rd fire risk unit should be based on fire risk, determine the unit's key management positions for fire safety.
Fire-risk fire safe key management positions, should be clearly responsible for fire safety management.
24th fire risk should be based on the characteristics, development of fire-fighting and emergency evacuation night production of fire risk, business unit, should develop a night-time fire-fighting and emergency evacuation plans.
Fire risk at least once every six months to organize a fire-fighting and emergency evacuation drills, and according to the walkthrough adjust the content of the fire-fighting and emergency evacuation plans.
25th fire units at high risk should be carried out in accordance with the regulations of the State fire safety inspections.
Public entertainment venues, hospitals, shopping malls, markets, labour-intensive enterprises and inflammable and explosive dangerous goods production, storage companies, such as at high risk of fire units, shall appoint a fire safety inspections in the production, business operations during continuous fire safety inspections.
Halls, theatres, museums, galleries, archives, sports halls and other fire-risk unit to host conferences, performances, exhibitions, sporting events and other activities, shall organize a continuous fire safety inspections.
The 26th fire risk of fire inspections, found in inspections for potential fire hazard, should take immediate measures to eliminate; not immediately eliminated, should develop a corrective action plan, the implementation of protective measures to ensure fire safety during the rectification.
27th against fire risk unit operating in the production, welding, gas welding, easy to produce an open flame of construction operations; construction needed in the production, business hours, construction work and production, should be effective fireproofing business areas and arrange for on-site childcare.
28th fire risk unit at least once every six months to staff a fire safety training for new posts and employees into new jobs should be job training in fire safety.
29th fire risk should be by posting pictures, radio, closed circuit television, to the staff of the unit the importance of fire safety, fire-fighting and evacuation, fire safety common sense.
Article 30th high-risk units to carry out fire prevention inspections, fire inspections, fire safety training, fire evacuation drills and fire hidden fire safety management activities, shall promptly record the message of fire safety management system.
Chapter III supervision article 31st fire unit consists of county-level public security fire control institutions identified at high risk and shall inform the unit.
Public security fire control institutions risk disagrees with the determination of the fire, from the date of receipt of the certificate of fire-risk units within 5th determination make written application for review the public security fire control institutions, public security fire control institutions shall from the date of receipt of the application within the 3rd reviewed and results will inform the applicant in writing.
Public security fire control institutions identified at high risk of fire units, reported by public security organs of the people's Government for the record and to the public, subject to public supervision.
32nd public security fire control institutions shall, in accordance with the laws, regulations and rules of the strictly carry out the fire fire safety supervision and administration in high risk units.
Public security fire control institutions belonging to the densely populated places at high risk of fire supervision and inspection at least once every quarter, at high risk of fire supervision and inspection at least once every six months.
33rd public security fire control institutions found significant fire potential fire risk unit, should be dealt with according to law in a timely manner, and to report to the public security organs, the people's Governments at the corresponding level supervision.
Fourth chapter legal responsibility 34th article violation this provides, has following case one of of, by police organ fire institutions ordered deadline corrected; late not corrected of, at 1000 Yuan above 3000 Yuan following fine: (a) fire water pipeline Shang not set valve right opening and closing of State identifies of; (ii) fire security focus parts not set fire Security identifies of; (three) not timely through fire security information management system entry fire security management situation, or in management system in the entry false information of.
35th article violation this provides, has following case one of of, by police organ fire institutions ordered deadline corrected; late not corrected of, at 2000 Yuan above 5000 Yuan following fine: (a) fire automatically alarm system not and City Fire Security remote monitoring system networking of; (ii) not by provides for fire facilities detection of; (three) not by provides for fire facilities maintenance maintenance of.
The 36th unit of public security fire control institutions staff at high risk for fires in fire safety management abuse, negligence, malpractice, shall be subject to punishment constitutes a crime, criminal responsibility shall be investigated according to law. Fifth chapter by-laws 37th article of the regulations come into force on January 1, 2016.